Často kladené otázky
Information: BGI 608 labeling of our products
The designation of BG regulations, rules, principles and information have changed in the past due to the reorientation and renaming of the BGs.
In this context, the former BGI 608 (Selection and operation of electrical systems and equipment on construction and assembly sites) has also been renamed several times.
BGI 608 → BGI/GUV-I 608 → DGUV Information 203-006
The old designation BGI 608 has become very widespread among the general public and is predominantly known to the relevant circles. On official BG websites, different designations are used in parallel (https://medien.bgetem.de/medienportal/artikel/QkdJIDYwOA--).
We have therefore decided to label our products with BGI 608 where applicable.
What connector systems are available through Brennenstuhl®?
Brennenstuhl® connector systems can be delivered to more than 150 countries around the world. You can find a detailed overview in the following list.
How can one tell if a cable drum or extension cord is suitable for outdoor use?
The cable reel or extension cord should be splash-proof. This is indicated through the marking IP44. Plugs must possess self-closing caps. The connection should also be sealing with a cap. The plug must have a sealing pod. For industrial or trade use, the cable must be of at least HO7RN-F or similar quality, i.e. XYMM. The cable quality and type of protection are crucial. brennenstuhl products are correspondingly marked in the catalogue.
Can the cable reel's overheating protection unit be purchased as a replacement part?
Yes, overheating protection for cable reels can be ordered through our sales department.
Which cable is suitable for which use?
When does the overheat control in case of cable drums trigger and how does it work?
The overheat control triggers if temperatures in the core of the drum are too high. Such high temperatures arise if the cable has not been unwinded sufficiently and heat arises due to high current flow to the connected consuming devices (coil effect). If the current has been interrupted by the overheat control swith (bi-metal), please unwind cable completely, unplug device and let cable unwinding device cool down. After a few minutes you can connect the mains plaug again and press the pushbutton on the plug plate shortly. The current flow should be restored now. Should this not be the case after a longer while, it may be possible that the switch gets damaged due to overload and needs to be replaced. As replacement is very easy, you can just request a replacement. An expert is able to replace the part within only a few minutes. However, it is easier to always use the device fully unwinded in order to prevent triggering of the overheat control.
Why must cable drums be completely rolled out for heavy-duty jobs?
Cable winding devices like cable reels or cable boxes can become very hot in the centre of the rolled-up cable. For this reason temperature switches (overheating protection) are stipulated to interrupt the current at around 65 degrees Celsius. Without this overheating protection, the cable insulation can melt and lead to destruction or fire of the winding device. To prevent an unnecessary premature switch-off of the electricity, the cable roll should be unwound.
Aké sú vlastnosti káblových bubnov Brennenstuhl®?
Rukoväť kyvadla ako rukoväť, na praktické zavesenie a ako vedenie kábla pri rozbaľovaní a stáčaní.
- ROL’UP Roll-up automatická
Pohodlné navíjanie krátkym ťahom namiesto dlhého naťahovania.
- Bretec® -Otočný kontakt comfort
Vďaka technológii rotačného kontaktu sa pri odvíjaní a odvíjaní otáča iba káblový bubon, nie vložka zásuvky.
- Zástrčka Garáž
Dva otvory v držadle kyvadla na uloženie zátky.
- Bubnová Brzda
Držiak kábla na tele bubna na pripevnenie kábla.